Concept and definition of machine room dynamic ring monitoring system
Do you have a little understanding of the concept and definition of the engine room dynamic monitoring system? Today, Shanghai Feirui Measurement and Control Technology Co., Ltd. gives you an explanation of the installation of explosion-proof cameras. Let's take a look.
The importance of the computer room is self-evident, and the professional computer room monitoring solution is an essential requirement for maintaining its safe operation. There is no management and real-time monitoring in place. When there is a problem, it will face unpredictable losses and costs. The standard engine room power environment monitoring system generally includes environmental temperature and humidity system, UPS equipment, power distribution monitoring system, air conditioning system. , fire system interface, water leakage monitoring system, access control management system, etc.
Briefly describe the above subsystems as follows:
First, temperature and humidity monitoring:
(1) When the data detected by any one of the temperature and humidity sensors exceeds the set upper or lower limit, the system monitors the host to issue a multimedia audible alarm or a telephone automatic dialing alarm, and immediately pops up a corresponding alarm window to notify the person on duty or the corresponding responsible person. .
(2) The system can set the upper and lower limits of temperature and humidity of each temperature and humidity sensor, display in real time (electronic map mode) and record the value of indoor humidity and temperature detected by each temperature and humidity sensor, display a section The curve of the change in time.
(3) The history of any monitored object can be queried.
Second, air conditioning monitoring:
(1) It can monitor and alarm the high-pressure fault of the compressor, the operating state of the air conditioner, the operating state of the air conditioner and the filter blockage in real time.
(2) The monitoring and control system can be used to control the start and stop of the air conditioner in the remote monitoring room and change the set value of temperature and humidity.
(3) Monitor the operating status of the precision air conditioner, display the working condition of the air conditioner with graphics and color changes, alarm when the fault occurs, and display and save the operating parameters, the status of each component and the alarm provided by each air conditioning communication protocol. Happening.
(4) When an alarm occurs, the alarm can be distinguished by the change of the corresponding color in the pop-up alarm window. At the same time, the system will issue a multimedia audible alarm or a telephone automatic dialing alarm to notify the person on duty or the corresponding responsible person.
(5) The history of any monitored object can be queried.
(6) Remote intelligent control of ordinary air conditioners, including switching machines, temperature regulation, mode switching, etc.
Third, UPS monitoring:
(1) Real-time judgment on whether the components of the UPS have an alarm. When a certain component of the UPS fails or exceeds the limit, the monitoring main system immediately pops up the corresponding alarm page window, and the monitoring host issues a multimedia sound alarm or a telephone automatic dialing alarm to notify the on-duty personnel. Or the corresponding responsible person.
(2) Real-time display and save the operating parameters and the status of each component that can be remotely monitored by each UPS communication protocol. You can query the history of any monitored object.
The above is the explosion-proof camera installation notes shared by Shanghai Feirui Measurement & Control Technology Co., Ltd., and more exciting information is waiting for you to discover.