GSP drug warehouse temperature and humidity monitoring system
▶GSP pharmaceutical drug warehouse environment temperature and humidity monitoring system
The system is based on the "Good Manufacturing Practices" (GSP regulations), for the monitoring and management system of environmental temperature and humidity in the circulation of pharmaceutical products. It is mainly used for remote monitoring and alarming of temperature and humidity of drug warehouses. The system provides strict monitoring and management of the temperature and humidity of the storage environment, and transmits the data to the PC for data storage and analysis, and outputs the printing curve. In the abnormal situation of the equipment, the corresponding personnel are notified by various forms of alarms to make the storage environment Surveillance is achieved by no one or few people, providing a strong guarantee for efficient management, use and safe operation of warehousing.
▶Related regulatory requirements
Article 4 The maximum allowable error of the system temperature and humidity measuring equipment shall meet the following requirements:
(1) The measurement range is between 0 °C and 40 °C, and the maximum allowable error of temperature is ±0.5 °C;
(2) The measurement range is between -25 °C and 0 °C, and the maximum allowable error of temperature is ±1.0 °C;
(3) The maximum allowable error of relative humidity is ±3% RH.
Article 5 The system shall automatically monitor and record the temperature and humidity environment during the storage and transportation of drugs. The system should update the temperature and humidity data of the measuring point at least every 1 minute. The real-time temperature and humidity data is automatically recorded at least every 30 minutes during the storage process, and the real-time temperature data is automatically recorded at least every 5 minutes during the transportation. When the monitored temperature and humidity are outside the specified range, the system should record the real-time temperature and humidity data at least every 1 minute.
Article 6 When the monitored temperature and humidity data reaches the set threshold or exceeds the specified range, and the system is interrupted by power supply, the system shall be able to realize the sound and light alarm at the local and at the designated place, and adopt SMS communication, etc. Not less than 3 designated personnel to report the alarm.
▶ monitoring software interface
▶Mobile device APP monitoring interface
- No next